True TUC-27F-LP-HC 27" Low Profile Undercounter Freezer
- 31 7/8" low profile height
- Eco-friendly R290 hydrocarbon refrigerant
White Glove Delivery - Available -What is White Glove service?
Standard common carrier delivery options cover the cost of getting an item to your shipping address but our White Glove delivery service does that and more!
The White Glove agent will call to schedule a delivery appointment within a four hour window, which gives you the flexibility to work around your busy schedule and to prepare the space where your item will be placed. Upon delivery, trained professionals will unload your item from the truck, bring it into the room of choice, unpack the item and remove all packaging debris from the premises.
Please note that White Glove delivery will typically add 5 - 7 business days to your order's transit, and only includes 30 minutes of on-site time. If on-site time beyond 30 minutes is required, you may be responsible for additional fees. Additionally, this service does not include set-up of the items being delivered.
"You May Also Need" items are guaranteed to work with the item you are viewing, such as lids that will fit a cup or casters that will fit a piece of equipment. If an item is not listed in this section, we do not guarantee that it will work with the product you are viewing and do not recommend that you purchase them for use together.
True 911299 White Coated Wire Half Shelf - 23 1/4" x 14"
True 883720 3" Swivel Stem Casters - 4/Set
True 830282 5" Swivel Stem Casters - 4/Set
True 983534 Gray Coated Wire Shelf - 23 1/4" x 16"
True 830280 2 1/2" Swivel Stem Casters with Silver Housings - 4/Set
Be sure to check out this video to learn how to clean your condenser on your True refrigerator! Step-by-step instructions are given on how to properly clean your condenser, and how to figure out how often you should be cleaning it.
Looking for a reliable undercounter and work top refrigerator? Try True’s TUC27 and TWT27! Both units have an oversized, balanced refrigeration system that ensures faster temperature recovery and shorter run times.
This video gives you helpful step-by-step instructions regarding the proper techniques for servicing various refrigerant systems. Whether you have a unit that runs on R290 or R-134A/404A, this video will assist you.
The goal of this video is to show you safely and correctly how to make a repair on any cabinet produced with R-290 refrigerant. The first thing to consider is, how do I identify the cabinet I'm working on uses R-290 refrigerant? All R-290 equipment is required to have special labeling throughout the cabinet. Besides the serial tag label, you'll see several labels on the cabinet interior and the back of the cabinet. Additionally, the condensing unit will have several labels on it. It is also required that all R-290 equipment have red sleeves over the refrigerant line process tubes.
Now that you've properly identified the cabinet as using R-290 refrigerant, also be aware that the cabinet was manufactured to meet specific UL guidelines and standards that pertain to R-290 refrigerant; because of this True requires any part used for the repair to be an OEM part. For any reason you receive a replacement part that is not exactly the same as the part you are replacing, stop and call True before continuing. All the fan motors have a sealed shaft. All the relay and temperature controls have sealed contacts. The wire connectors that we use require a certain amount of force to pull the wires out of the connectors, which eliminates any spark potential. Wire nuts and crimp type connectors do not meet this requirement, therefore, they should never be used in any R-290 cabinet.
For all refrigeration repairs, you're still required to follow good refrigeration practices. Standard refrigeration tools will still be required including oxygen free dry nitrogen, a micron gauge, and shut off valve for your charging hose. In addition to these tools, you should also use as short of a refrigerant hose, as possible, as well as a pinch off tool. Now let's focus on the additional specialized tools that will be required for R-290 service. You will need a combustible gas leak detector, the safety placard, use only R-290 refrigerant. If you're using the 1 lb. cylinder supply by True, you will also need to use the specialized charging valve. These are the only specialized tools needed to service an R-290 system. True offers these parts individually or as part of several types of R-290 repair kits. Please contact True's parts department for pricing and availability.
The following procedure should be followed when doing any type of refrigeration repair. True requires the following good refrigeration practices, these should practices should include, but are not limited to: not leaving the refrigeration system open to the atmosphere for more than 15 minutes, always change the dryer whenever the refrigeration system has been opened, use a micron gauge, and pull a vacuum to a minimum of 500 microns. The introduction to the refrigeration system of anything other than a flushing agent, nitrogen, R-290, or refrigerant oil is prohibited. All refrigeration repair should be made in a well ventilated area. The repair we are going to show is replacing a condensing unit on an R-290 system that was previously diagnosed with a locked-up compressor.
Our R-290 repair starts with a service technician turning on his combustible gas leak detector and leaving it on throughout the unit repair. When you turn on the combustible gas leak detector it will have to self-calibrate, this will take about a minute. Once the high-pitch beeping levels off, you can continue. Do not proceed with the repair until the meter levels off. Put on your safety glasses. The technician should then display the safety placard in the area he will be making the repair in. Disconnect the unit you're repairing from any power source. The service technician will then need to install temporary piercing valves to allow access to the refrigeration system. To do this, you may need to trim a portion of the required red identifying sleeves back and place the temporary valves as close to the crimp on the end of the process tube, as possible. The combustible gas leak detector may go off during this process. Once the high-pitch beeping levels off, you can proceed.
After the temporary valves have been placed on the suction and discharge process tubes on an R-290 system, the technician will have to install his manifold gauge set with a short of hoses as possible on each of the temporary valves. Once again, the combustible gas leak detector may briefly go off. Wait for your meter to level off, then proceed with the repair. To remove the refrigerant from the system, you can open up both the high and low side lines and release the refrigerant slowly into the atmosphere. Doing this will more than likely set the combustible gas meter off. You should immediately shut off both valves on your manifold and allow any release R-290 refrigerant to dissipate in the atmosphere. Once the combustible gas meter levels off, you can continue to release R-290 refrigerant, repeating this process until all the refrigerant has been released from the refrigeration system. Once the refrigerant is out of the system, the technician must use a tubing cutter to cut out any failed refrigeration component. The reason for this is to prevent any possible spread of contamination and for the overall safety factor. For this example, the technician will cut the compressor pull out right where it brazes into the compressor. He would then cut the liquid line as it exists the dryer. If the technician is replacing the compressor, he would cut the compressor discharge line right as it exits the compressor instead of the liquid line as it exits the dryer.
Once the condensing unit has been removed, you will set the new condensing unit into place. Before pulling the plugs out of the compressor ports, be sure all of your refrigeration lines have been cleaned, pre-fitted, and are ready to be installed. This will minimize the amount of time the refrigeration system is open, which reduces the potential for any moisture to be absorbed into the compressor oil. When brazing on an R-290 system, you must always purchase oxygen free dry nitrogen through the system for a minimum of two minutes before and during brazing. We recommend you set the nitrogen regulator between 3-5 psig. Start to purge the nitrogen through the high side process tube, allowing it to exit out the suction process tube. You can now start to braze all of the joints.
Once all brazing is done and the solder joints have cooled, pressurize the system with no more than 200 psig of oxygen free dry nitrogen to leak check. Once we know that there are no leaks, you're ready to evacuate the refrigeration system. Release the nitrogen charge down to about 2 lbs. of nitrogen pressure to ensure that no outside air is being drawn into the refrigeration system. Connect your charge hose to your micron gauge, that should have already been connected to your vacuum pump. Start pulling a vacuum as soon as possible to help remove any moisture from the system. Continue to pull a vacuum until you reach a minimum of 500 microns. Once you reach 500 microns, you will want to close off the shut off valve on the charging hose as well as the high and low side lines on your manifold gauges. Remove the charging hose going to your micron gauge. Place the adapter valve on the 1 lb. R-290 cylinder. Be sure to leave the R-290 cylinder in its box. Then attach a charging hose to the R-290 adapter valve, place the cylinder in the box on its side on the charging scale. Open up the tank valve, then bleed the charging hose. We recommend placing something heavy on top of your charging hose so that if the hose gets pulled, it will not affect the scale. Zero out the scale. Open up the shut off valve on the charging hose. R-290 can be added as a liquid or a vapor. Open up the high side valve until the desired charge has been weighed in, then close the valve. If the system didn't take it's full charge, close the high side valve and start the compressor and allow it to run for a minute. Then slowly open the low side valve until fully charged. Once the system is fully charged, close the adapter valve on the R-290 cylinder as well as the shut off valve on the charging hose. Allow the unit to run to verify operation.
It is now time to remove both your hoses and temporary access valves. True requires the removal of any access valves on any refrigeration system. The next step would be to remove the refrigerant that is trapped in the high side hose to assure that we have proper charge in the unit. To do this, pinch off the high side process tube in front of the access port. Next, you want to open up the high side valve, then slowly open the low side manifold valve to draw all the refrigerant out of the high side hose. Once the pressures have equalized, you can close the high and low side manifolds. Using a tubing cutter, cut the high side process line in front of the temporary access valve, behind the pinch off tool. This could cause the combustible leak detector to go off. Wait for the combustible gas leak detector to level off before moving on. Be sure to crimp the end of the copper tube down, so that it will make it easier to weld. Test the end of the line with the bubble to make sure it's not leaking. Once the combustible gas leak detector levels off, you're ready to braze the end of the process tube shut. Once the process tube cools down, remove the pinch off tool and thoroughly leak check with soap bubbles. Now you can repeat these steps for the low side process tube. Once the final repair's completed, if the red identifying process tube sleeves have been removed, they must be reinstalled once the process tubes have cooled down.
If you have any questions prior to working on an R-290 system, stop and contact True's technical service department at 1-855-372-1368 or 1-800-325-6152.
Are you curious about how to properly repair your True R-290 refrigerant system? Check out this informative how-to video for an in-depth look on the service process.
Maintain your environmentally-friendly, R-290 refrigeration equipment to help promote durability and longevity! By charging the refrigeration system yourself, you can save both time and money while ensuring that your equipment is in tip-top shape.
With environmental concerns on the rise, True refrigeration is taking the necessary steps to prepare for the future. Check out this video to learn more about hydrocarbon refrigeration and its impact on the world around us.
Learn the ins and outs of the True TUC and TWT undercounter and worktop refrigerators and freezers!
|Width||27 5/8 Inches|
|Depth||31 1/8 Inches|
|Height||31 7/8 Inches|
|Interior Width||26 1/4 Inches|
|Interior Depth||24 5/8 Inches|
|Interior Height||26 1/4 Inches|
|Compressor Location||Rear Mounted|
|Compressor Style||Side / Rear Breathing|
|Energy Star Qualified||Yes|
|Made in America||Yes|
|Number of Doors||1|
|Number of Shelves||2|
|Temperature Range||-10 Degrees F|
Customer questions about this product
- How do I know if this unit will fit under or match the height of my ADA-Height counter?
- Many manufacturers offer their refrigeration equipment in several different height options to best meet your needs. Here's a breakdown of how we classify these different heights:
Counter Height: Work surface is more than 34" high; standard height unit.
ADA Height: Work surface height is less than 34"; complies with ADA regulations.
Low Profile: Work surface height is less than 32"; designed to fit under most ADA-height counters.
If the unit you are purchasing does not have a flat top, such as a worktop or sandwich/salad prep table, it may affect whether or not it will align with certain countertops. To ensure that the product will meet your needs, please reference the product's literature and specifications.
- I haven’t heard of R290, R600a, or R513a refrigerant before. What is it?
- R290 (also known as high purity propane or CARE 40) and R600a (also known as refrigerant grade Isobutane or CARE 10) are hydrocarbon refrigerants. R513a (also known as Opteon XP10) is an HFO (hydrofluoroolefin) refrigerant. They are being used as an eco-friendly refrigerant by some manufacturers in response to the EPA’s Significant New Alternatives Policy (SNAP) Program. Read more about this program in our blog post on Refrigerant Regulations.
- Why is there a step in the interior of this undercounter unit?
- This unit’s refrigeration system is located in the lower rear of the cabinet, causing the step in its interior. The step may decrease the inner depth of the cabinet's lower interior versus what is listed as its overall interior depth, so please check the unit’s specs and diagrams to ensure it will accommodate your storage needs.
The 27" wide True TUC-27F-LP-HC low profile undercounter freezer is ideal for tight spaces at your busy establishment! Its 1 1/2" diameter casters lower its working height to just 31 7/8", for space-limited situations like underneath custom millwork. Two adjustable, heavy duty PVC coated wire shelves help you keep the interior organized no matter what you're storing. Designed for maximum performance and efficiency, the True TUC-27F-LP-HC low profile undercounter freezer will provide years of dependable service.
- Solid stainless steel front, ends and countertop; self-closing door with 90 degree stay-open feature
- Aluminum finished back; clear coated aluminum interior with stainless steel floor
- 1/3 hp compressor, R290 refrigerant with Ozone Depletion Potential of 0 and Global Warming Potential of 3
- Foamed in place polyurethane insulation maintain -10 degrees Fahrenheit; automatic defrost
- 2 adjustable, heavy duty PVC coated wire shelves
- 1 1/2" casters reduce working height, enable easy mobility during cleaning
Width: 27 5/8"
Depth: 31 1/8"
Height: 31 7/8"
Depth: 24 5/8"
Height: 26 1/4"
This Item Ships via Common Carrier. For more information and tips to help your delivery go smoothly, click here.
This item meets the standards imposed by NSF International, which focuses on public safety, health, and the environment.
Made in America
This item was made in the United States of America.
Energy Star Qualified
This item has been Energy Star Qualified by the US Environmental Protection Agency and the US Department of Energy, making it an energy-efficient product.
UL US & Canada
This item has been tested and meets safety standards imposed by the Underwriters Laboratories (UL) for use in the United States of America and Canada.
This unit comes with a NEMA 5-15P plug.
A PDF viewer is required to view this product's information. Download Adobe Acrobat software
PLEASE NOTE: This is not a replacement warranty. Units purchased in 2013 or later will have a 3 year parts and labor warranty; units purchased prior to 2013 will have a 1 year parts and labor warranty. RESIDENTIAL USERS: Vendor assumes no liability for parts or labor coverage for component failure or other damages resulting from installation in non-commercial or residential applications. The right is reserved to deny shipment for residential usage; if this occurs, you will be notified as soon as possible.
|True Refrigeration TUC-27F-LP (Formerly)|
Other Products from this Line
True TUC-60F-LP 60" Low Profile Undercounter Freezer
Turbo Air TUF-48SD Super Deluxe 48" Undercounter Freezer - 12 Cu. Ft.
Continental Refrigerator SWF36-U 36" Low Profile Undercounter Freezer - 10.3 Cu. Ft.
Traulsen ULT72-LL 72" Undercounter Freezer with Left Hinged Doors - 20 Cu. Ft.
People Talk About:True's products stand Webstaurant True shop refunded more manufacturers Love
Love True products. They are a bit more than their competitors but they stand by their warranty which is longer than most other manufacturers and they stand by their products. Built to last. There was a shipping issue which wasn't True's fault by any means but either way Webstaurant took care of and fully refunded the shipping costs. That's why we shop at Webstaurant!
Jacob A. from 5 Stones Coffee Co LLC Posted on 02/11/2016
Get paid to review this product!
If you've used this product, simply log in and share your text, video, and photo reviews of it. The customers on the left did it, and you can too! Earn up to $16.00 per product.Login or Register